DC circuit breakers

Knowing the electrical characteristics of direct current and its differences in comparison with alternating current is fundamental to understand how to employ direct current. Direct current presents different problems than alternating current with a regard to the phenomena associated to the interruption of high value currents since the arc extinction results to be particularly difficult.

Usually DC sources are low voltage like batteries and such, so you don’t associate DC with sparking, but it will, especially when voltages get considerably higher than 12 or 24V (Common DC voltage levels to get idea of different DC voltage levels in use). Take a look at this AC versus DC load breaking comparison with a knife switch video that clearly shows the difference in electrical contact by alternating current to direct current:

Yes, DC sparks much more aggressively than AC. When a switch carrying DC is opened, the current being interrupted is always equal to the current flowing in the circuit. When interrupting an AC current, the current varies with time, and, on average, is less than the peak current (it normally goes to zero during mains power zero crossings). For this reason, a given switch normally has 2 current; one for AC current, and a lower one for DC current. It can also have different voltage ratings for AC and DC. This applies to practically all components that switch electrical current: switches, relays, fuses and circuit breakers.

Switching resistive DC load is hard, and switching off inductive load is even harder. Why does a switch spark when disconnecting a coil carrying high dc current? article tells that the reason is that an inductor resists a change in current. If you have a steady state current going through an inductor and you attempt to suddenly decrease the current to zero by opening the circuit, the inductor will respond by attempting to maintain the current, but that current has nowhere to go. This creates a large negative voltage spike across the inductor. It is very common to see transients of several hundred or thousand volts. This is why you need often to have some kind of suppression circuit in place. Breaking DC is considerably harder than AC. For example many small relays that have 250VAC 10A rating have only 30VDC rating for the same current!

The next question is can I use AC circuit breaker for DC? Can I use an AC circuit breaker in a DC circuit discussion says that most AC breakers are rated at least for 120VAC. Some of them will also mention a DC rating which is usually like one-fifth of the AC voltage rating (24V DC). The reason for the downgrading is that with AC the voltage dips down to zero every 120th of a second, giving the spark across the opening contacts a chance to snuff out. With DC there is no such helpful time and the sparks can continue to jump across a much longer distance than AC sparks. Assuming your batteries are 24V or less, then a 120VAC breaker that also says “24VDC” should work.

In Finland the mains voltage is 230V like it is all over Europe. Here the circuit breakers are rated for 230V or higher (400V for three phase power). I have seen several 230V breakers with 48VDC voltage ratings. So with such would be suitable for 48VDC. When you check the DC voltage rating, check also if other data is different for DC (for example maximum current breaking capacity and operation current of magnetic trip device). For typical battery powered systems (up to 24 VDC), those standard 230 or 400 VAC circuit breakers will probably work, but it is best to check that from the manufacturer data sheet. If your breakers are rated for 48VDC, then battery voltages up to 48V are OK with them. I have also seen some dual circuit breakers that are rated for 415VAC and 110V DC.

AC DC Circuit Breaker – Can DC trip an AC breaker? video shows how AC circuit breaker being used in a DC circuit and how it trips when overloaded. It gives good introduction to using AC circuit breaker for DC, but I do not agree on the the conclusions on the trip current difference on AC and DC (thermal trip can take quite a bit of time with double the rated current on both AC and DC):

Generally AC circuit breakers will trip on DC and but at higher currents and voltages extinguishing of the arc may be an issue and a potential fire hazard. Typically the thermal trip remains typically the same but magnetic tripping can need higher current to operate than with AC (note that the magnetic trip on most AC breakers is set approximately 5-10 times the breaker rating on AC operation). ﻿You﻿ need to consult the manufacturers specifications for thermal trip times (for example a 10 amp breaker can take 30 secs to trip at 20 amps, 1 sec at 60 A, 10ms at 100A).

ABB circuit-breakers for direct current applications document says that the thermal magnetic trip units fitted to a.c. circuit-breakers are also suitable to be used with direct current. The part relevant to the thermal protection does not change with reference to its tripping characteristic since the bimetal strips of the trip units are influenced by the heating caused by the current flow, it does not matter whether alternating or direct: in fact the bimetal strips are sensitive to the r.m.s. value. As regards the instantaneous protection against short-circuit, due to ferromagnetic phenomena, the instantaneous tripping occurs at a different value in comparison with the analogous case in alternating current.

Really bad things can happen if the breaker does not trip when it should and if it can’t break the DC current you feed to it. DO NOT try this with an AC breaker that does not have a DC rating! A 6 Amp AC breaker trips on DC at 240 Volts 30 Amps video does not recommend an AC breaker for DC applications because of potential fire hazard when extinguishing of the arc has issues with DC:

There are special circuit breakers for DC applications. The bigger DC breakers even have a magnet near the contacts to try to bend the arc away from the shortest path. You need special DC breakers especially in applications where you handle few hundreds of volts DC (for example large solar power systems and DC power distribution as used in some data centers). For information on DC breakers check ABB circuit-breakers for direct current applications document. It says that Miniature circuit-breakers series S280 UC comply with Standard IEC 60947-2 and differ from the standard versions in that they are equipped with permanent magnetic elements on the internal arcing chambers (allow the electric arc to be broken up to voltages equal to 440VDC). The presence of these permanent magnetic elements establishes the circuit-breaker polarity (positive or negative); as a consequence, their connection shall be carried out in compliance with the polarity indicated on the circuit-breakers. An incorrect connection of the polarities could damage the circuit-breaker.

So there are special cautions related to use of circuit breakers designed for DC applications in mind: There are types need to be installed carefully in the right way (plus/minus connection and input/output sides). DC Circuit Breaker Fires video shows the difference of right and wrong installation:

For details on correct wiring check Correct Wiring Of Double Pole DC Breakers – Clean Energy Council. A number of the breakers on the market (e.g. ABB, GE and Terasaki) only have the ‘+’ and ‘–‘ symbols on one side and a number of the breakers on the market (e.g. Clipsal, Klockner Moeller)) have the + and – symbols on both the top and bottom terminals. These can cause confusion. The positive and negative outputs of power source must be connected to the respective ‘+’ and ‘–‘ terminals on the circuit breaker. Non polarised circuit breakers operate safely as load breaking isolators and for fault current protection regardless of the direction of current flow through them.

So when working with DC circuits, read carefully the technical specifications of the circuit breakers and other components you plan to use to make sure they are suitable for the task and you connect them to the circuit in the right way. Always use a direct current rated fuse or circuit breaker in a direct current system.

1. Newport Brass Nb3 230b 56 Divertersays:

Simply citing this blog post everyone will agree with it because its correct so its pleasant to see a poster thats stating snippets such as this publically to review

2. Pro Pacsays:

Evidently reading the above topic readers will agree with this because it is correct and it’s good spotting an op thats showing this online to look at.

3. Renovationssays:

Excellent blog! I’ll keep keeping an eye out for more of your posts in future.

4. Tomi Engdahlsays:

ABB Advance Makes Renewable-Energy Supergrids Practical

A high-power circuit breaker makes it possible to create highly efficient DC power grids.

ABB, the large power and automation company, has developed technology that could provide an efficient way to transmit power from widely distributed solar panels, wind turbines, and other sources of renewable energy. The new technology is a fast and efficient circuit breaker for high-voltage direct-current (DC) power lines, a device that has eluded technologists for 100 years. The breaker makes it possible to join high-voltage DC transmission lines to form a resilient power grid.

If renewable energy is ever to account for a large part of the total energy supply, countries will need to install new, large-scale transmission grids, both to get power to cities from remote areas such as deserts that often have the best renewable resources, and to combine power from widely distributed wind turbines and solar panels, which can help average out fluctuations in their output. In Europe, there’s been talk for years of a supergrid that would pull together power from hydroelectric dams in Scandinavia with wind farms in Germany and large solar farms in Spain and even North Africa

But such a supergrid has faced serious technical hurdles.

The transmission lines that make up conventional power grids use alternating current (AC), which loses large amounts of power over long distances unless complicated and expensive measures are taken. DC is more efficient over long distances, and it offers the additional benefit of working well underground and underwater, reducing or eliminating the need for the unsightly transmission towers that can make it difficult to site new transmission lines.

ABB’s circuit breaker changes that. Within five milliseconds it can stop the flow of a huge amount of power—equal to the entire output of a nuclear power plant, ABB says.

Researchers have been trying to develop high-voltage DC circuit breakers for a century (see “Edison’s Revenge: The Rise of DC Power”). Mechanical switches alone didn’t work—they shut off power too slowly. Power electronics made of transistors that can switch on and off large amounts of power offered a possible solution, but they proved far too inefficient. ABB’s solution combines power electronics with a mechanical switch to create a hybrid system that’s both fast and efficient.

“The hybrid breaker should be less costly.”

5. Karl says:

Hi there
Can anyone explain to me why DC voltage should be switched in series, i.e. if you have a 2-pole breaker that can handle 400VDC then it appears that by installing a link across the two poles the breaker can safely isolate 800V through the 2 switches. Is this possible to do in parralel as well or does the DC voltage require series?
Regards
Karl

• tomisays:

Direct current presents different problems than alternating
current with aregard to the phenomena associated
to the interruption of high value currents since the arc
extinction results to be particularly difficult.

This extinction involves
energetic phenomena which depend on the voltage level
of the plant (Un) and lead to install circuit-breakers according
to connection diagrams in series to the advantage
of the performances under short-circuit conditions
(as a matter of fact, the higher is the number of contacts
opening the circuit, the higher is the breaking capacity
of the circuit-breaker).

This means that, when the voltage rises, it is necessary
to increase the number of current interruptions in
series, so that a rise in the arc voltage is obtained and
consequently a number of poles for breaking operation
suitable to the fault level.

6. katrina says:

Good job! Full of information, everyone that will read this blog will get so much to learn. Thanks! very helpful

7. John Delanskisays:

Relectric is a national supplier of new and reconditioned used and obsolete circuit breakers, electrical distribution and control equipment. http://www.relectric.com

8. Amy Parsonssays:

Great explanation. Electrical currents are so dangerous and so many precautions need to be taken when working with electrical currents. If you need a UPS backup for your equipment then I suggest you check out http://switchon.eaton.com.

9. Tomi Engdahlsays:

Tripping Out: A Field Guide to Circuit Protection

Residential breakers in North America come in a couple of different flavors. The branch circuit breakers are used to protect each branch circuit – the outlets, light fixtures, and appliances that are connected in parallel back to the main panel. Each branch circuit is typically rated for either 15 or 20 amps, and unless it’s running a large load like an electric dryer or a well pump, it’ll be a 120-volt circuit. In addition to the branch breakers, a panel will have a main breaker to catch any faults that a defective branch breaker misses

10. Tomi Engdahlsays:

AC versus DC load breaking comparison with a knife switch

AC Circuit Breaker 230V DC Test

11. Tomi Engdahlsays:

Breakers AC, DC & AC/DC – Solar Safety Part 2 – 12v Solar Shed

12. Tomi Engdahlsays:

DC Circuit Breakers at Your Local Hardware Store

Great topic post. You can use SQ D QO series breakers single pole or 2 pole up to 48 VDC. (Bought from home depot, lowes, electrical supply)You must derate the AIR rating from 10,000 to 5,000. The one major difference between AC breakers and DC is AC breakers do not have a high arc rating for the contacts like DC breakers do. The DC arc is much stronger. A non rated DC breaker could fuse together upon this arcing. The SQ D QO series is good from 10-70VDC. They are also the only ones i know of to buy off the shelf. if your using a 12 or 24v system there are other automotive fuses that can be used that are cheaper and just as effective.

The Square D ckt breakers (QOs) are ok for the lower voltage DC Solar Feeds, however for those (like myself) that want the higher voltage and lower current, Solar Feeds (IE: for those long runs from the PV Panels to the Charge Controller) the Square D “Heavy Duty” Fused Disconnect (they are DC rated) are a better choice! If properly configured!!! …much mis-information on the WEB about configuration/wiring and/or what components to use in your Solar Powered System!

Great Bit if info for those one a tight budget. I run a 48 volt system and I have solar volts up to 80 volts and later I will have up to 130 volts DC from solar, so I have to spend more on the more costly breakers, I use Din rail breakers on my system, Your right they are costly that is for sure. Seems the higher the amperage the higher the breakers cost.

Square D QO, Square D Home Line Difference

Very interesting reading about dc and breakers, I have learnt something new

This is very good reading i learnt a lot

15. Tomi Engdahlsays:

AC Circuit Breaker 230V DC Test

Arc died only because contacts melted away.
This is what will happen if you install AC breaker into DC circuit, for example PV circuit.
And don’t try this at home kids.

MCB Popping (or why you don’t protect DC loads with an AC breaker)

This is why you don’t protect high-voltage or high-current DC loads with an AC breaker. If this was high current (instead of high voltage) the outcome would have been similar, just much more rapidly

16. Tomi Engdahlsays:

A.C. CIRCUIT BREAKER VERSUS CAR BATTERY!!

17. Tomi Engdahlsays:

MCB Testing at DC

MCB short circuit test by dc voltage

18. Tomi Engdahlsays:

AC Circuit Breaker 230V DC Test

Arc died only because contacts melted away.
This is what will happen if you install AC breaker into DC circuit, for example PV circuit.

MCB short circuit test by dc voltage

here i show u MCB short circuit protection test with 150Ah 12 volt lead acid battery the ratting of mcb is 16 amp 240,450 volt

Thanks for the information about DC breakers i have learnt alot from this post

21. Tomi Engdahlsays:

DC Circuit Breaker Fires

AC Circuit Breaker 230V DC Test

22. Tomi Engdahlsays:

MCB Popping (or why you don’t protect DC loads with an AC breaker)

This is why you don’t protect high-voltage or high-current DC loads with an AC breaker.

Most 230V AC breakers are ok for up to 50VDC﻿

23. Tomi Engdahlsays:

A Dramatic Demo of AC Versus DC Switching

Switches seem to be the simplest of electrical components – just two pieces of metal that can be positioned to either touch each other or not. As such it would seem that it shouldn’t matter whether a switch is used for AC or DC. While that’s an easy and understandable assumption, it can also be a dangerous one, as this demo of AC and DC switching dramatically reveals.

As dramatic as the demo is, it doesn’t mean we won’t ever be seeing DC in the home. It just means that a little extra engineering is needed to make sure that all the components are up to snuff.